A hydrostatic test is a way in which pressure vessels such as pipelines, plumbing, gas cylinders, boilers and fuel tanks can be tested for strength and leaks. The test involves filling the vessel or pipe system with a liquid, usually water, which may be dyed to aid in visual leak detection, and pressurization of the vessel to the specified test pressure. Pressure tightness can be tested by shutting off the supply valve and observing whether there is a pressure loss. The location of a leak can be visually identified more easily if the water contains a colorant. Strength is usually tested by measuring permanent deformation of the container. Hydrostatic testing is the most common method employed for testing pipes and pressure vessels. Using this test helps maintain safety standards and durability of a vessel over time. Newly manufactured pieces are initially qualified using the hydrostatic test. They are then re-qualified at regular intervals using the proof pressure test which is also called the modified hydrostatic test. Testing of pressure vessels for transport and storage of gases is very important because such containers can explode if they fail under pressure.
Hydrostatic tests are conducted under the constraints of either the industry’s or the customer’s specifications, or may be required by law. The vessel is filled with a nearly incompressible liquid – usually water or oil – pressurised to test pressure, and examined for leaks or permanent changes in shape. Red or fluorescent dyes may be added to the water to make leaks easier to see. The test pressure is always considerably higher than the operating pressure to give a factor of safety. This factor of safety is typically 166.66%, 143% or 150% of the designed working pressure, depending on the regulations that apply. For example, if a cylinder was rated to DOT-2015 PSI (approximately 139 bar), it would be tested at around 3360 PSI (approximately 232 bar). Water is commonly used because it is cheap and easily available, and is usually harmless to the system to be tested. Hydraulic fluids and oils may be specified where contamination with water could cause problems. These fluids are nearly incompressible, therefore requiring relatively little work to develop a high pressure, and is therefore also only able to release a small amount of energy in case of a failure – only a small volume will escape under high pressure if the container fails. If high pressure gas were used, then the gas would expand to V=(nRT)/p with its compressed volume resulting in an explosion, with the attendant risk of damage or injury. This is the risk which the testing is intended to mitigate.
Portable fire extinguishers are safety tools that are required to be on hand in almost every public building. Fire extinguishers are also highly recommended in every home. Over time the conditions in which they are housed, and the manner in which they are handled affect the structural integrity of the extinguisher. A structurally weakened fire extinguisher can malfunction or even burst when it is needed the most. To maintain the quality and safety of this product, hydrostatic testing is utilized. All critical components of the fire extinguisher should be tested to ensure proper function.
Pipeline & frequency test
Hydrotesting of pipes, pipelines and vessels is performed to expose defective materials that have missed prior detection, ensure that any remaining defects are insignificant enough to allow operation at design pressures, expose possible leaks and serve as a final validation of the integrity of the constructed system. ASME B31.3 requires this testing to ensure tightness and strength.
Buried high pressure oil and gas pipelines are tested for strength by pressurizing them to at least 125% of their maximum allowable working pressure (MAWP) at any point along their length. Since many long distance transmission pipelines are designed to have a steel hoop stress of 80% of specified minimum yield strength (SMYS) at MAOP, this means that the steel is stressed to SMYS and above during the testing, and test sections must be selected to ensure that excessive plastic deformation does not occur.
Test pressures need not exceed a value that would produce a stress higher than yield stress at test temperature. ASME B31.3 section 345.4.2 (c)
Other codes require a more onerous approach. BS PD 8010-2 requires testing to 150% of the design pressure – which should not be less than the MAOP plus surge and other incidental effects that will occur during normal operation.
Leak testing is performed by balancing changes in the measured pressure in the test section against the theoretical pressure changes calculated from changes in the measured temperature of the test section.
Australian standard AS2885.5 “Pipelines—Gas and liquid petroleum: Part 5: Field pressure testing” gives an excellent explanation of the factors involved.
Most countries have legislation or building code that requires pressure vessels to be regularly tested, for example every two years (with a visual inspection annually) for high pressure gas cylinders and every five or ten years for lower pressure ones such as used in fire extinguishers. Gas cylinders which fail are normally destroyed as part of the testing protocol to avoid the dangers inherent in them being subsequently used.
These common gas cylinders have the following requirements:
- DOT-3AL gas cylinders must be tested every 5 years and have an unlimited life.
- DOT-3HT gas cylinders must be tested every 3 years and have a 24-year life.
- DOT-3AA gas cylinders must be tested every 5 years and have an unlimited life. (Unless stamped with a star (*) in which case the cylinder meets certain specifications and can have a 10-year hydrostatic test life).
Typically organizations such as ISO, ASTM and ASME specify the guidelines for the different types of pressure vessels.